Radiator Connection Fitting 1"||شد وصل
All installations made using PEX PIPE, such as FIRAT PEX underfloor heating systems, FIRAT PEX mobile heating systems, FIRAT PEX clean water systems are also used as fittings. In the body, inner parts and fittings of Fırat Pex Pipe Metal Fittings, MS 58 brass material is used, and EPDM O-Ring is used to ensure tightness.
PEX PIPE Metal Fittings are produced in accordance with TS EN 1254-3 standard. In accordance with TS EN 1254-3 standard, the following tests are applied to Pex Pipe Metal Fittings.
Leak Test Under Pressure,
Separation Strength Test
Thermal Cycle Test
Pressure Cycle Test
Tensile Corrosion Resistance Test
Coating Thickness Determination Test (It is applied to the material other than standard tests.)
Pex Pipe Metal Fittings Installation and Usage Information
The installation pressure should not exceed 10 bar and the operating temperature should not exceed 105 ° C.
Attachments must be installed by a qualified plumber.
Any foreign matter (dirt, sand etc.) in the installation must be cleaned before installation.
Attachments should be used with original fittings.
Suitable sealing materials (Teflon tape) should be used on the threaded parts of the fittings.
During assembly, the attachment must be tightened with a suitable key from the key mouth parts.
Abrasive materials should not be used for attachment cleaning.
The installation must be protected against the risk of frost.
It should be protected against external impacts during storage, transportation, assembly and use.